Generic selectors
Exact matches only
Search in title
Search in content
Post Type Selectors

Aegis

# Can Inductive Absorbers Substitute for Shaft Grounding?

By: Aegis

AEGIS recently received an email from an engineering consultant. He had specified a project that requires AEGIS Shaft Grounding Rings for motors controlled by variable frequency drives. Then a contractor put in a bid including common mode chokes or inductive absorbers, not shaft grounding. The contractor said that they do the same thing as shaft grounding. Well, the engineer wanted to know, is that true?

They do not. To see why, let’s have a look at what drives’ output looks like, and then talk about what each of these devices does.

#### What is Common Mode Voltage?

VFDs put out pulses of voltage in each of the three phases. The average of the three phase voltages is called common mode voltage (top graph, blue), and it is never zero. The average of the phase currents, the common mode current (bottom graph), is near zero most of the time, but it jumps every time the common-mode voltage changes.

#### The Difference Between Common Mode Voltage and Shaft Voltage

When the common mode voltage reaches the motor, it couples to the rotor by capacitance. This creates a so-called shaft voltage (top, orange). This part is important: The higher the common mode voltage, the higher the shaft voltage produced. When the shaft voltage gets too high, it will discharge by arcing through the bearings. This is shown around time = 18 on the graph: the shaft voltage drops suddenly, the smoking gun of an arc. The same thing happens around time = 115, but starting from negative shaft voltage.

This arcing causes electrical bearing damage, and it is a problem in all motors on drives. AEGIS rings prevent this damage by bleeding off shaft voltage before it gets high enough to discharge through the bearings.

Common mode & shaft voltage, & common mode current, with inductive cores.

#### How Do Inductive Absorbers Work?

Inductive absorbers work totally differently. They decrease the peak common mode currrent, as shown in the second set of graphs. They also decrease the slope of the common mode voltage, i.e., how fast it changes. (Jargon alert: they decrease dv/dt.) But inductors do not change the maximum size/height of the common mode voltage, so they will not prevent shaft voltage buildup and discharge.

#### Types of Electrical Bearing Damage

In fairness, inductive cores do have their uses. In addition to shaft voltage discharge, there are two other types of electrical bearing damage: High-frequency circulating current in large motors, over 100 HP/75 kW, and rotor ground current in poorly grounded motors. Inductive absorbers decrease both of those bearing currents, and they also reduce stray/noise current from the drive.

But they do not affect shaft voltage buildup and discharge, and so cannot replace AEGIS Shaft Grounding Rings.

AEGIS Rings also come with a 2-year extended warranty against bearing fluting damage. No other form of protection against VFD-caused bearing damage offers a warranty like this.

To learn more about AEGIS shaft grounding and best practices for electrical bearing protection, sign up for a training. They offer monthly live training webinars, and – pandemic restrictions permitting – they can also visit your facility to review your exact application.

# Why Should You Care About the Total Cost of Owning an Electric Motor?

Previously, Aegis discussed Volume 3 of the 2021 MSMA report on potential savings through improved efficiency. Let's expand on how…

# Are Insulated Bearings Susceptible To Electrical Damaged?

A couple of months ago, Aegis published a Q&A post including an account of electrically damaged insulated bearings. Aegis got…

## Related Whitepapers

### Expansion Joint Expertise Improves Industrial Wastewater System Reliability

The majority of industries have wastewater treatment plants. Government agencies and local governments require these facilities to meet pretreatment requirements. Pretreatment rules were enacted to prevent…

### How to Decrease Oil Changes with Bearing Isolators [Inforgraphic]

Learning how to decrease oil changes can be time- and money-saving. Oil life can be long if contamination is eliminated, which is easier said than…

### Synchronous Machines Are The Optimal Choice For Heavy Industry

TECO-Westinghouse experience assures superior performance and reliability For over a century, Westinghouse has been the pacesetter in the design and production of electric machines for heavy…

### Why FLEXXORs Are Designed Differently

J. Hilbert Anderson, President of Coupling Corporation of America, discusses some of the reasons why FLEXXORs are designed differently from all other flexible couplings, and…