Generic selectors
Exact matches only
Search in title
Search in content
Post Type Selectors

Aegis

# Can Inductive Absorbers Substitute for Shaft Grounding?

By: Aegis

AEGIS recently received an email from an engineering consultant. He had specified a project that requires AEGIS Shaft Grounding Rings for motors controlled by variable frequency drives. Then a contractor put in a bid including common mode chokes or inductive absorbers, not shaft grounding. The contractor said that they do the same thing as shaft grounding. Well, the engineer wanted to know, is that true?

They do not. To see why, let’s have a look at what drives’ output looks like, and then talk about what each of these devices does.

#### What is Common Mode Voltage?

VFDs put out pulses of voltage in each of the three phases. The average of the three phase voltages is called common mode voltage (top graph, blue), and it is never zero. The average of the phase currents, the common mode current (bottom graph), is near zero most of the time, but it jumps every time the common-mode voltage changes.

#### The Difference Between Common Mode Voltage and Shaft Voltage

When the common mode voltage reaches the motor, it couples to the rotor by capacitance. This creates a so-called shaft voltage (top, orange). This part is important: The higher the common mode voltage, the higher the shaft voltage produced. When the shaft voltage gets too high, it will discharge by arcing through the bearings. This is shown around time = 18 on the graph: the shaft voltage drops suddenly, the smoking gun of an arc. The same thing happens around time = 115, but starting from negative shaft voltage.

This arcing causes electrical bearing damage, and it is a problem in all motors on drives. AEGIS rings prevent this damage by bleeding off shaft voltage before it gets high enough to discharge through the bearings.

Common mode & shaft voltage, & common mode current, with inductive cores.

#### How Do Inductive Absorbers Work?

Inductive absorbers work totally differently. They decrease the peak common mode currrent, as shown in the second set of graphs. They also decrease the slope of the common mode voltage, i.e., how fast it changes. (Jargon alert: they decrease dv/dt.) But inductors do not change the maximum size/height of the common mode voltage, so they will not prevent shaft voltage buildup and discharge.

#### Types of Electrical Bearing Damage

In fairness, inductive cores do have their uses. In addition to shaft voltage discharge, there are two other types of electrical bearing damage: High-frequency circulating current in large motors, over 100 HP/75 kW, and rotor ground current in poorly grounded motors. Inductive absorbers decrease both of those bearing currents, and they also reduce stray/noise current from the drive.

But they do not affect shaft voltage buildup and discharge, and so cannot replace AEGIS Shaft Grounding Rings.

AEGIS Rings also come with a 2-year extended warranty against bearing fluting damage. No other form of protection against VFD-caused bearing damage offers a warranty like this.

To learn more about AEGIS shaft grounding and best practices for electrical bearing protection, sign up for a training. They offer monthly live training webinars, and – pandemic restrictions permitting – they can also visit your facility to review your exact application.

# Variable Frequency Drives in Cold Weather Environments

Aegis frequently discusses various applications that can benefit from controlling electric motors with variable frequency drives (VFDs). From the deepest…

# Mining Operations with Variable Frequency Drives

Mining has been vital to civilization since at least the Bronze Age. In today’s electrified world, metals and minerals are…

# AEGIS Rings: Resilience Beyond Resistance

Installing Colloidal Silver When an AEGIS ring is installed with colloidal silver on the shaft, the resistance from frame-to-shaft is often…

## Related Whitepapers

### Driving Energy Savings a Commercial Facility Energy Upgrade Project

Upgrading to Design Envelope pumps helped GAC save energy costs of 20,000 AED in the first year. Armstrong’s Pump Manager service provides reports and notifications…

### Submersible Pump Monitoring Chesterton Connect™ System Solves Pump Maintenance Challenges in the Wastewater Industry [Ebook]

Chesterton Connect™ System Detected Vibration Caused by Ragging Issues in Submersible Pumps Helping Prevent Pump Damage Sewage treatment is a type of wastewater treatment which…

### Contra-Rotating Axial Fan Design Concept for Leaf Blowers

It seems leaf blowers are everywhere in our neighborhoods, very often disturbingly noisy. There is a need for excellent aerodynamic and aeroacoustics design for such…

### Split Seal + SpiralTrac® Solution Reduces Maintenance and Water Use

A wastewater treatment facility has 10 RAS (Return Activated Sludge) solids handling pumps. These pumps have been sealed using packing and replacement sleeves for several…