Generic selectors
Exact matches only
Search in title
Search in content
Post Type Selectors

Engineered Software Inc.

Below are the answers for the Engineered Software Inc. Brain Teaser #1 – Static Head in Piping Systems.

1. B-90ft
2. B-90ft
3. B-90ft
4. C-95ft
5. A-87ft

Explanations:

Elevation Head = (Elevation of product tank liquid surface) – (Elevation of supply tank liquid surface)

System #1:
Static Head = (100 ft + 10 ft) – (0 ft + 20 ft) = 90 ft

System #2:
Even though the pipe enters the middle of the tank at 105 ft elevation, there is still another 5 ft of liquid above the pipe penetration. The discharge of the pump “feels” a column of water that is 110 ft high, and the suction feels 20 ft of water from the supply tank. Static Head = (105 + 5) – (0 + 20) = 90 ft

System #3:
Even though the pipe rises to 120 ft elevation, it drops back down and discharges at 105 ft elevation and there is still another 5 ft of liquid above the discharge of the pipe. The energy it takes to raise the fluid from 105 ft to 120 ft going up is recovered by the siphon effect as the fluid drops from 120 ft to 105 ft to the outlet. The net effect is that the pump still has 110 ft of head it has to push against at the discharge and 20 ft of head at the suction to help it. Static Head = (105 + 5) – (0 + 20) = 90 ft.

System #4:
The outlet of the pipe is at 115 ft elevation, even though it rises to 120 ft then drops back down (5 ft of energy is recovered due to the siphon effect). Static Head = (115) – (20) = 95 ft
(NOTE: When just starting up, the pump has to overcome 100 ft of static head to reach the top of the loop)

System #5:
Since static head is in reference to the fluid going through the pump, System 5 requires a density compensation of the 85 ft of liquid from the heat exchanger to the product tank. Check out the related article from our Knowledge Base that talks about how to do it.

The density of water at 200 F is about 60.1 lb/ft^3, and at 60F it’s about 62.4 lb/ft^3.

85 ft x (60.1/62.4) = 81.9 ft.

Total static head = (static head from pump to HX + head from HX to product tank – head from supply tank to pump)

Total static head = (25 ft + 81.9 ft) � 20 ft = 86.9 ft.

The net effect of the temperature (density) compensation is to reduce the static head by 3 ft to 87 ft.

___________________________________________

If you have a suggestion or a Brain Teaser you would like to suggest, please send and email to brainteaser@eng-software.com.

We welcome your suggestions and feedback on any of the Ask an Engineer articles.

___________________________________________

� 2011 Engineered Software, Inc. 4529 Intelco Loop SE, Lacey, Washington 98503
www.eng-software.com

# Create a Virtual System Model in 11 Steps

Author: Dominik Fry, P.E., Engineered Software, Inc. Plant processes have become more intricate with a host of supervisory control and data…

# Learn How to Model Piping Systems with FLO-Master Training

When: November 6 - 7, 2018 Where: Houston, Texas  (Click here for the Webinar or learn about on-site training at your…

# Piping System Brain Teaser #2: How does a fluid’s properties affect a centrifugal pump’s performance?

Manufacturers typically test centrifugal pumps with water to develop a pump performance curve that they provide to their customers. But…

## Related Whitepapers

### CFturbo BLADERUNNER Centrifugal End-Suction Pump Casestudy

The CFturbo BLADERUNNER 2024 is a unique and innovative tool that will outperform the known capabilities of an automated simulation process for Turbomachinery performance maps.…