Generic selectors
Exact matches only
Search in title
Search in content
Post Type Selectors

Aegis

# Harmonics and Bearing Currents-the Other Side of the Drive

By: Aegis

An attendee at a recent webinar asked EST-AEGIS about electrical bearing damage by harmonic currents created by VFDs.  Bearing currents from harmonics are very different from the usual type of VFD-sourced bearing current because they are on the line/supply side of the drive.  The bearing currents which is normally talk about are on the load side.  Harmonics don’t get talked about a lot, but they were happy to explain.

VFDs work by rectifying ac current and storing it in a capacitor bank (the dc bus).  Basically, whenever the voltage in a phase is higher than the dc bus voltage, current will flow in to charge the capacitors (Figure 1 – note that in a three-phase system, you actually get two current pulses per voltage peak, but the idea is the same.)  This makes VFDs nonlinear loads.

A linear load draws a steady sinusoidal current from the supply.  A nonlinear load is any device that does not draw a smooth sinewave of current from the supply.  Here’s an analogy:  Driving a linear load is like pushing a well-maintained shopping cart.  You can push it smoothly along with no jerks or snags.  A nonlinear load is like pushing a cart with a sticky wheel that jams every two steps, and you need to shove it to get it moving again.  Not smooth.

Nonlinear loads are a problem because they distort the supply voltage and current.  Look at Figure 1 again.  The drive only draws occasional pulses of current, not a smooth sinewave.  If you think of the power supplied by a utility or generator as a large sinewave, drawing out those occasional pulses will put dents in the supply current wave, distorting it.  Distorted current in turn distorts the voltage waveform.

Without getting into Fourier series, you can treat the distortion as being caused by waves with frequencies that are whole number multiples of the supply frequency (50/60 Hz).  These higher-frequency waves (at 100/120 Hz, 150/180, etc.) are called harmonics, and they are introduced to the supply by nonlinear loads, including drives.

This causes several problems… upstream of the drive, elsewhere in the facility.  Having many drives or other large nonlinear loads in a facility can cause problems not only with other circuits in the facility itself but in other nearby facilities served by the same utility.  These problems include interference with sensors; overheating transformers, motors, and generators; and, yes, bearing currents.  And again, harmonics generated by one drive can attack motors other than the one controlled by that drive.

Harmonics produce (relatively) low-frequency circulating currents in motors.  Like high-frequency circulating currents in larger motors powered by drives, harmonic circulating currents can be mitigated with one insulated bearing.  Unlike VFD-caused high-frequency circulating current, they are best mitigated by reducing the supply’s harmonic content.  Harmonic mitigation is a field in itself.  For a fuller discussion of harmonics and their mitigation, see this newsletter from Trane (Ingersoll Rand) or this presentation from the Power & Energy Institute of Kentucky.

As for this post, the takeaway is that the bearing currents produced by harmonics are separate from what we normally call VFD-caused bearing current.  The big difference is that mitigating harmonics will not reduce shaft voltage discharge, high-frequency circulating current, or rotor ground current.  For those, you respectively need AEGIS® shaft grounding, an insulated bearing opposite the grounding ring, and good bonding back to the drive or a grounding strap between the motor and load frames.

# Safeguarding Bearings with AEGIS PRO Grounding Rings: A Cement Manufacturer’s Solution

The squealing seemed unstoppable, though the Monarch Cement Company's massive ball mill was already quite loud. Powered by a 5,000-HP…

# Boosting Power Generation Reliability with Shaft Grounding

The modern world relies fundamentally on electric power. As electrification continues to expand into sectors such as transportation and HVAC,…

# Safeguarding Generator Gearboxes with AEGIS Shaft Grounding

When discussing shaft grounding, it's typically AC motors that come to mind for most people. But a generator is basically…

## Related Whitepapers

### Upside Down Condos [Case Study]

This condo tower (324 units on 13 floors) had completed a previous retrofit that unfortunately left the variable speed pumps operating in a fixed mode…

### Ras Al Khaimah saves 20% energy and 12% OPEX in wastewater pumping system

RAKWA is the RAK wastewater agency responsible for designing, building, operating, and maintaining all the public wastewater systems. Ras Al Khaimah—known as RAK—is the northernmost…

### Intelligent Pumps Exceed Savings Estimates (Commercial Facility Installation Casestudy)

Design Envelope 6800 boosters reduced energy consumption by 76% compared to previous boosters, resulting in annual cost savings of \$4,400 per system. Background The Heron’s…

### Centaur’s Wireless Battery-powered Gateway

Our Solution Wireless sensors combined with a wireless battery-powered gateway can provide a flexible, safe, cost-effective, and reliable solution for collecting continuous condition monitoring data…